A guide to selecting the right float switch for your application
By Simon Dear of Cynergy3 Components
When selecting a float switch for a liquid level sensing application, a number of factors need to be considered, including float switch and gasket materials, physical arrangement, electrical ratings and cable type, says Simon Dear of Cynergy3 Components.
Many industrial processes require devices that are able to sense the level of liquid stored within various types of tank or chamber. The signals from these devices may be used to control the production process or to provide indication of the status.
One of the most reliable, well-proven technologies for liquid level sensing is a float switch. This type of switch comprises a magnet contained within a float, as well as a magnetic reed switch contained within a fixed housing. The movement of the float, due to the changing liquid level, will cause the reed switch to operate (i.e. close or open) at a particular level. This tried and trusted technology is based on a relatively simple design that offers long term reliability without the need for the user to calibrate the switch.
Whilst there are different methods available for selecting the right float switch for a particular application, the main factors to consider include the following:
Physical arrangement and style
The choice of styles that may be suitable for an application will depend on the physical arrangement of the tank, the available mounting positions and whether access is available to the inside of the tank. The main styles are horizontal/side mounting and vertical mounting. The horizontal/side mounting type normally has a fixed housing, which passes through the sidewall of a tank, with a hinged float attached to the fixed housing. Vertical mounting types normally have a fixed vertical stem, which is installed through the top or bottom of a tank, along which slides a cylindrical float.
Another important consideration is whether a build up of deposits from the liquid on the float body is likely to occur. These deposits can, over a period of time, accumulate to such an extent that the float switch can fail to operate. Whilst particular types of float switch have been developed to limit the effects of this build up, the experience and knowledge of the switch manufacturer is also critical here.
It is critical to select a float switch that is constructed from the right materials that are compatible with the liquids and temperatures of the particular application. Component damage as a result of incorrect materials selection can ultimately cause failure of a float switch, which may have severe consequences. Typical float switch materials include:
Nylon: suitable for many oils, diesel, organic chemicals and MEK-based printing inks.
Polypropylene (PP): suitable for many acids and alkali, detergents, inorganic and organic chemicals, oils and water.
Polyphenylene sulphide (PPS): suitable for many of the more aggressive chemicals and higher process temperatures, up to 120ºC.
Buna/Nitrophyl: suitable for many oils, diesel, petrol and water (non-potable applications).
D300 foam (PVC): suitable for most hydraulic oils and many chemical solutions.
Stainless steel: suitable for most medical and food applications, chemicals, hydraulic fluids, fuel oils and applications with process temperatures up to 135ºC.
Selection of the most suitable materials for both float switch and gasket can be made by referring to a ‘Chemical Compatibility’ table. These tables provide a good indication of the suitability of the various float switch materials in a wide range of liquids. For some process liquids, it may be necessary to obtain a sample float switch in order to test the compatibility.
It is important to fully understand the nature of the load that needs to be switched and to ensure that the float switch is capable of handling this load. The electrical ratings, which most manufacturers provide in their float switch specifications, are for purely resistive loads. Any loads that have either inductive or capacitive components should have the appropriate contact protection measure applied.
In applications where aggressive liquids may spill onto external wiring, it is important to specify particular materials for the cables used to connect to the float switches. There are standard, UL-approved cable types for the various float switches, as well as high temperature, low smoke zero halogen (LSZH) and other specialised materials.
Custom engineered float switches
The operating environment is critical to the choice of float switch. A water tank for an industrial process may only require a simple plastic float switch. However, if the application is in a hazardous area, for example, a petrochemical storage tank where flammable gases, vapours or dust are present, a stainless steel, explosion-proof float switch will be required.
Over the years, Cynergy3 has custom engineered many variants of its float switches to match particular customer requirements in a wide range if industry sectors including oil, gas & petrochemicals; food and beverage; chemicals and pharmaceuticals; water and wastewater; and process manufacturing. These include float switches for all types of environment, including industrial process control, safe areas, intrinsically safe and hazardous areas (ATEX-certified), as well as WRAS-approved switches for drinking water applications.
Cynergy3 is a manufacturer of liquid level and flow sensors, HV and RF relays. The company has developed an extensive range of liquid level sensors over the past 44 years by focusing on solutions for customer applications. Cynergy3 has been at the forefront of RF relay technology for 30 years, during which time it has developed relays for many specific communications applications, by working with world leading manufacturers of radio communications equipment.
How to Select a Control Systems Integrator
By Patrick Supanich, Contributor
As an end user, you must rely more and more on outside engineering services for your automation needs. Choosing...
Factory of the Future: From Vision to Reality
By Andy Chang, NI
The Factory of the Future is a research and technology initiative aimed to push emerging technologies to improve the...
PID Control Using a Data Acquisition and Control System
By Terry Nagy, Computer Aided Solutions
The architecture of data acquisition and control systems which have their own DSP processors makes them...
Reinventing manufacturing with the latest technologies
By Bill Lydon, Editor
There is a great opportunity to leverage the latest technologies and compete in the global manufacturing landscape. The...
EtherNet/IP Fully Harnesses the Power of Industrial IP
By Paul Brooks, Rockwell Automation
Manufacturers around the world have adopted EtherNet/IP as their information infrastructure, and hundreds of...
Aveva to supply virtualization software to platform in North Sea
AVEVA Activity Visualisation Platform will be used to improve operational training on Total’s Martin Linge topside platform in the North Sea
Barry-Wehmiller Expands in Texas
Three new offices opened in early 2015 in Ft. Worth, Houston, and San Antonio.
Rotork acquires Masso
Masso is a manufacturer of shipboard valve remote control systems (VRCS).
Automation Federation releases report on virtualization in control systems
Report examines the use of virtualization technology in industrial automation and control system (IACS) environments.
CSIA appoints José M. Rivera as CEO
Rivera brings decades of global experience in the automation industry to his new role at CSIA, having worked in six countries, primarily in...