A guide to selecting the right float switch for your application
By Simon Dear of Cynergy3 Components
When selecting a float switch for a liquid level sensing application, a number of factors need to be considered, including float switch and gasket materials, physical arrangement, electrical ratings and cable type, says Simon Dear of Cynergy3 Components.
Many industrial processes require devices that are able to sense the level of liquid stored within various types of tank or chamber. The signals from these devices may be used to control the production process or to provide indication of the status.
One of the most reliable, well-proven technologies for liquid level sensing is a float switch. This type of switch comprises a magnet contained within a float, as well as a magnetic reed switch contained within a fixed housing. The movement of the float, due to the changing liquid level, will cause the reed switch to operate (i.e. close or open) at a particular level. This tried and trusted technology is based on a relatively simple design that offers long term reliability without the need for the user to calibrate the switch.
Whilst there are different methods available for selecting the right float switch for a particular application, the main factors to consider include the following:
Physical arrangement and style
The choice of styles that may be suitable for an application will depend on the physical arrangement of the tank, the available mounting positions and whether access is available to the inside of the tank. The main styles are horizontal/side mounting and vertical mounting. The horizontal/side mounting type normally has a fixed housing, which passes through the sidewall of a tank, with a hinged float attached to the fixed housing. Vertical mounting types normally have a fixed vertical stem, which is installed through the top or bottom of a tank, along which slides a cylindrical float.
Another important consideration is whether a build up of deposits from the liquid on the float body is likely to occur. These deposits can, over a period of time, accumulate to such an extent that the float switch can fail to operate. Whilst particular types of float switch have been developed to limit the effects of this build up, the experience and knowledge of the switch manufacturer is also critical here.
It is critical to select a float switch that is constructed from the right materials that are compatible with the liquids and temperatures of the particular application. Component damage as a result of incorrect materials selection can ultimately cause failure of a float switch, which may have severe consequences. Typical float switch materials include:
Nylon: suitable for many oils, diesel, organic chemicals and MEK-based printing inks.
Polypropylene (PP): suitable for many acids and alkali, detergents, inorganic and organic chemicals, oils and water.
Polyphenylene sulphide (PPS): suitable for many of the more aggressive chemicals and higher process temperatures, up to 120ºC.
Buna/Nitrophyl: suitable for many oils, diesel, petrol and water (non-potable applications).
D300 foam (PVC): suitable for most hydraulic oils and many chemical solutions.
Stainless steel: suitable for most medical and food applications, chemicals, hydraulic fluids, fuel oils and applications with process temperatures up to 135ºC.
Selection of the most suitable materials for both float switch and gasket can be made by referring to a ‘Chemical Compatibility’ table. These tables provide a good indication of the suitability of the various float switch materials in a wide range of liquids. For some process liquids, it may be necessary to obtain a sample float switch in order to test the compatibility.
It is important to fully understand the nature of the load that needs to be switched and to ensure that the float switch is capable of handling this load. The electrical ratings, which most manufacturers provide in their float switch specifications, are for purely resistive loads. Any loads that have either inductive or capacitive components should have the appropriate contact protection measure applied.
In applications where aggressive liquids may spill onto external wiring, it is important to specify particular materials for the cables used to connect to the float switches. There are standard, UL-approved cable types for the various float switches, as well as high temperature, low smoke zero halogen (LSZH) and other specialised materials.
Custom engineered float switches
The operating environment is critical to the choice of float switch. A water tank for an industrial process may only require a simple plastic float switch. However, if the application is in a hazardous area, for example, a petrochemical storage tank where flammable gases, vapours or dust are present, a stainless steel, explosion-proof float switch will be required.
Over the years, Cynergy3 has custom engineered many variants of its float switches to match particular customer requirements in a wide range if industry sectors including oil, gas & petrochemicals; food and beverage; chemicals and pharmaceuticals; water and wastewater; and process manufacturing. These include float switches for all types of environment, including industrial process control, safe areas, intrinsically safe and hazardous areas (ATEX-certified), as well as WRAS-approved switches for drinking water applications.
Cynergy3 is a manufacturer of liquid level and flow sensors, HV and RF relays. The company has developed an extensive range of liquid level sensors over the past 44 years by focusing on solutions for customer applications. Cynergy3 has been at the forefront of RF relay technology for 30 years, during which time it has developed relays for many specific communications applications, by working with world leading manufacturers of radio communications equipment.
Perspectives on Digital Transformation: A Look at the Future of Automation Through the Eyes of Dell
By Bill Lydon, Editor, Automation.com
The Dell EMC World 2016, in October, was a thought-provoking experience, where Dell set forth their bright...
Empowering the Workforce to Control the Future of Automation
By Peter Martin, Schneider Electric Process Automation
Connected products are expected to approach 30 billion by 2020, with utilities,...
DHS Best Practices to Secure ICS Communications
By Daniel Crum, Owl Computing Technologies, Inc.
The US Department of Homeland Security, in conjunction with the FBI and NSA, has released...
How Smart Instruments Enable Improved Pumping
By Nathan Hedrick, Endress+Hauser
Several instrument manufacturers offer various types of “smart instruments,” and their approaches vary. This...
Is MES On Its Way Out?
By Bill Lydon, Editor, Automation.com
The convergence of IT and OT is one of the more fascinating trends that has spawned many discussions...
Wireless Switches & Sensors - New Control Possibilities
By Steute USA
Clearly, wireless technology has been widely accepted and embraced in the industrial community. This has resulted in the development...
Schneider Electric recognizes 50th anniversary of SimSci process simulation solution
SimSci process simulation solutions serve 23 of the world’s top 25 petroleum companies; 48 of the top 50 chemical companies; and all of the top...
Endress + Hauser earns IACET accreditation for IACET Continuing Education Units (CEUs)
Upcoming classes in 2017 which offer CEUs at Endress+Hauser include I-101 Basic instrumentation in January, March, June, and September in...
T&M Associates announces Victor Acosta as CAD Manager
Acosta brings nearly 20 years of experience in implementing design standards and quality procedures and leveraging burgeoning technologies to...
Okuma to highlight automated machining advancements at NTMA Plant Managers Roundtable
The NTMA Plant Managers Roundtable at Modern Industries in Phoenix, Arizona will discuss the various types of automation devices that make...