ABB adds SIS to Natural gas dehydration facility
Located near a field of producing wells in western USA, the facility has safety critical points at each of several manifolds that share the total flow of raw gas being processed. One such manifold, as indicated Figure 1, has gas inputs coming through pipes from five wells in one area of the well field. Gas from the wells ranges in pressure up to 3,000 psi in insulated, underground pipe specified for these high pressures.
Removal of free and entrained water is done in two consecutive process steps. Both steps occur in pipe and vessels rated at 1,600 psi, which must be protected from possible pressure excursions at the manifolds. Once free and entrained water is removed from the natural gas, it flows via pipeline to another plant that separates it into such products as methane, carbon dioxide, hydrogen sulfide, nitrogen, and helium. Dehydration and separation of the raw gas are normally continuous processes occuring in sequence.
Originally, the dehydration facility operated with a basic Distributed Control System (DCS) to reduce gas pressures at the manifolds to 1,500 psi, as required to remove free water. The facility depended on pressure safety valves installed within the downstream process areas to shunt any overpressure gas to a flare stack.
Protecting lower pressure equipment
Growing demands for natural gas resulted in upstream supply pressures at the manifolds to near the maximum allowable. At this point engineers conducted a risk analysis study that indicated need for independent SIS protection at piping locations vulnerable to serious overpressures. The risk study also determined that a Safety Integrity Level (SIL) of 2 would be sufficient for all the components of an SIS -- sensor, logic solver, and final control element.
In this application, the SIS sensors are a pair of electronic DP transmitters from ABB to measure each critical pressure point -- set at 1,510 psi on a PLC SIL 2 logic solver. The final control elements are ball valves installed in each high-pressure supply pipe -- two valves in series to provide proper SIL for safety shut-off in case of overpressure.
The facility chose ABB 2600T series pressure transmitters having SIL-2 ratings certified by the German test agency TÜV. SIL-2 pressure transmitters work in pairs to monitor safety critical points. A pair of ABB SIL-2 rated pressure transmitters offers the same protection as three redundant conventional pressure transmitters.
Generally the installed and operating cost of specialized transmitters is far less than that of the required conventional transmitters to meet a specific SIL value. Set at 1510 psi the SIS catches an overpressure condition and shuts the ball valves in the high pressure piping within affected manifolds. This action takes place before any pressure safety valve vents, eliminating this possible source of undesirable emissions.
ABB is a leader in power and automation technologies that enable utility and industry customers to improve their performance while lowering environmental impact. The ABB Group of companies operates in around 100 countries and employs about 107,000 people.
MORE CASE STUDIES
Honeywell's Experion Orion Console boosting plant efficiency
More than 130 Experion Orion Consoles have been sold globally. One of the earliest implementations of Experion Orion Console was at ICL Brasil’s...
FIPA builds End-of-Arm-Tooling to enhance FANUC robotics
Built in FIPA’s American facilities, and installed in the testing and demonstration laboratory at FANUC headquarters in Rochester Hills,...
Emerson Industrial's Unidrive AC delivers power for German textile company
Freudenberg needed to replace an AC drive within their nonwoven production facility in Kaiserslautern, Germany. The need for a small footprint...
Heaven Hill Brands selects Westfalia Technologies to automate Bardstown facility
Using Westfalia’s automated storage and retrieval system (AS/RS) integrated with a layer pick system, Heaven Hill will optimize the storage and...
Surlean Foods chooses noax' industrial hardware for weighing and packaging in custom-food...
To meet customers’ complex custom-batch processing requirements, Surlean Foods chose noax industrial touchscreen computers to support their...
NEMA publishes NEMA ABP 1-2016 Selective Coordination of Low-Voltage Circuit Breakers
The purpose of this paper is to provide guidance to engineers regarding the National Electrical Code (NEC) requirements for selective coordination.
7 Myths of Version Control & Backups in Automated Production
This whitepaper tackles the seven most common myths and misconceptions surrounding version control and data management in the current technological...
TrendMiner announces $1.1 Million funding from The Innovation Fund
This is a symbolic investment after the Fund’s recent series A funding to TrendMiner of $6 million in December 2015. The investment group...
The past, present and future of smart factories
Technavio recently published a report detailing the top three emerging trends impacting the Global RTLS Market for industrial applications to 2020,...
Eclipse Automation joins newly formed Smart Automation Group
This partnership – which includes Eclipse Automation, Insys Industriesysteme AG, Transmoduls Ltd, SMZ Wickel-und Montagetechnik AG, JULI...