ABB adds SIS to Natural gas dehydration facility
Located near a field of producing wells in western USA, the facility has safety critical points at each of several manifolds that share the total flow of raw gas being processed. One such manifold, as indicated Figure 1, has gas inputs coming through pipes from five wells in one area of the well field. Gas from the wells ranges in pressure up to 3,000 psi in insulated, underground pipe specified for these high pressures.
Removal of free and entrained water is done in two consecutive process steps. Both steps occur in pipe and vessels rated at 1,600 psi, which must be protected from possible pressure excursions at the manifolds. Once free and entrained water is removed from the natural gas, it flows via pipeline to another plant that separates it into such products as methane, carbon dioxide, hydrogen sulfide, nitrogen, and helium. Dehydration and separation of the raw gas are normally continuous processes occuring in sequence.
Originally, the dehydration facility operated with a basic Distributed Control System (DCS) to reduce gas pressures at the manifolds to 1,500 psi, as required to remove free water. The facility depended on pressure safety valves installed within the downstream process areas to shunt any overpressure gas to a flare stack.
Protecting lower pressure equipment
Growing demands for natural gas resulted in upstream supply pressures at the manifolds to near the maximum allowable. At this point engineers conducted a risk analysis study that indicated need for independent SIS protection at piping locations vulnerable to serious overpressures. The risk study also determined that a Safety Integrity Level (SIL) of 2 would be sufficient for all the components of an SIS -- sensor, logic solver, and final control element.
In this application, the SIS sensors are a pair of electronic DP transmitters from ABB to measure each critical pressure point -- set at 1,510 psi on a PLC SIL 2 logic solver. The final control elements are ball valves installed in each high-pressure supply pipe -- two valves in series to provide proper SIL for safety shut-off in case of overpressure.
The facility chose ABB 2600T series pressure transmitters having SIL-2 ratings certified by the German test agency TÜV. SIL-2 pressure transmitters work in pairs to monitor safety critical points. A pair of ABB SIL-2 rated pressure transmitters offers the same protection as three redundant conventional pressure transmitters.
Generally the installed and operating cost of specialized transmitters is far less than that of the required conventional transmitters to meet a specific SIL value. Set at 1510 psi the SIS catches an overpressure condition and shuts the ball valves in the high pressure piping within affected manifolds. This action takes place before any pressure safety valve vents, eliminating this possible source of undesirable emissions.
ABB is a leader in power and automation technologies that enable utility and industry customers to improve their performance while lowering environmental impact. The ABB Group of companies operates in around 100 countries and employs about 107,000 people.
MORE CASE STUDIES
ABB's Dodge CST drive system improves conveyor reliability at Norwegian mine
ABB’s Dodge controlled start transmission (CST) drive system is helping prevent repeated breakdowns of a 700 meter (m) conveyor at a Norwegian...
Control Techniques magnet motor reduces energy usage for dairy producer
The solution, which also features a Leroy-Somer Powerdrive high-power modular drive, is being used in an industrial refrigeration system that cools...
Cognex and Carter Controls provide automatic ID readers for vitamin retailer warehouse
The challenge for the integrator that designed and installed the automation system was to find an ID reader that could deliver near 100% read...
Renishaw joins Airbus efforts to automate aircraft wing manufacturing
The £17.7 million project, being led by Airbus in the UK, is to develop an innovative way of designing and manufacturing aircraft wings, which...
Prediktor's Apis software used by Statoil as OPC UA gateway
The overall objective of the delivery is to provide a standardized and unified way of accessing operational data from different assets via...
Real World Results When Demand-Driven Production Planning and Scheduling is Synchronized
By Thomas R. Cutler and John Maher
In today’s complex manufacturing environments, the physical processes of manufacturing involve so many moving...
Axiomtek partners with SYSCON-PlantStar to facilitate Asian manufacturing
Axiomtek is a design and manufacturing company in the industrial and embedded computer field. The company also employs an international service...
ABB announces 2nd edition of Single Loop Control Methods
The objective of Single Loop Control Methods is to help make the complicated subject of process control more easily understood by process engineers...
Industrial Wired vs. Wireless Networking on the CNC Shop Floor
In order to improve efficiency and remote management on the CNC shop floor, networking is required from both device level and infrastructure...
MicroPower Direct releases glossary of power conversion terms
MicroPower Direct's free power conversion glossary contains 19 pages and 800 definitions of terms associated with a range of power technologies and...