ABB adds SIS to Natural gas dehydration facility
Located near a field of producing wells in western USA, the facility has safety critical points at each of several manifolds that share the total flow of raw gas being processed. One such manifold, as indicated Figure 1, has gas inputs coming through pipes from five wells in one area of the well field. Gas from the wells ranges in pressure up to 3,000 psi in insulated, underground pipe specified for these high pressures.
Removal of free and entrained water is done in two consecutive process steps. Both steps occur in pipe and vessels rated at 1,600 psi, which must be protected from possible pressure excursions at the manifolds. Once free and entrained water is removed from the natural gas, it flows via pipeline to another plant that separates it into such products as methane, carbon dioxide, hydrogen sulfide, nitrogen, and helium. Dehydration and separation of the raw gas are normally continuous processes occuring in sequence.
Originally, the dehydration facility operated with a basic Distributed Control System (DCS) to reduce gas pressures at the manifolds to 1,500 psi, as required to remove free water. The facility depended on pressure safety valves installed within the downstream process areas to shunt any overpressure gas to a flare stack.
Protecting lower pressure equipment
Growing demands for natural gas resulted in upstream supply pressures at the manifolds to near the maximum allowable. At this point engineers conducted a risk analysis study that indicated need for independent SIS protection at piping locations vulnerable to serious overpressures. The risk study also determined that a Safety Integrity Level (SIL) of 2 would be sufficient for all the components of an SIS -- sensor, logic solver, and final control element.
In this application, the SIS sensors are a pair of electronic DP transmitters from ABB to measure each critical pressure point -- set at 1,510 psi on a PLC SIL 2 logic solver. The final control elements are ball valves installed in each high-pressure supply pipe -- two valves in series to provide proper SIL for safety shut-off in case of overpressure.
The facility chose ABB 2600T series pressure transmitters having SIL-2 ratings certified by the German test agency TÜV. SIL-2 pressure transmitters work in pairs to monitor safety critical points. A pair of ABB SIL-2 rated pressure transmitters offers the same protection as three redundant conventional pressure transmitters.
Generally the installed and operating cost of specialized transmitters is far less than that of the required conventional transmitters to meet a specific SIL value. Set at 1510 psi the SIS catches an overpressure condition and shuts the ball valves in the high pressure piping within affected manifolds. This action takes place before any pressure safety valve vents, eliminating this possible source of undesirable emissions.
ABB is a leader in power and automation technologies that enable utility and industry customers to improve their performance while lowering environmental impact. The ABB Group of companies operates in around 100 countries and employs about 107,000 people.
MORE CASE STUDIES
Kepware's KEPServerEX helps HIROTEC enable IIoT connectivity
HIROTEC selected Kepware’s KEPServerEX connectivity software and the ThingWorx IoT Platform to enable company-wide device-to-cloud connectivity...
Emerson Industrial delivers motor control to oilfield cranes
A US-based specialist in the supply of complete electrical packages for oil rig cranes is using Control Techniques AC and DC drives as part of a...
KUKA robots work with University of Stuttgart on automated sewing process
The university in Stuttgart combines bionic investigations with innovative robotic manufacturing methods
Elite Control Systems brings process control to Scotland whiskey distillery
This combination of technology and 24-hour technical support will ensure that the automated control systems that Edrington uses to operate the new...
GE to help Spirit Aerosystems forward to the Industrial Internet
Looking to increase production of critical aviation industry products, Spirit AeroSystems will implement Efficiency Analyzer on Predix, GE’s...
Six Steps to Using the IoT to Deliver Maintenance Efficiency
By Kevin Terwilliger, Dell
This article discusses ways to utilize advanced IoT technology to enable successful predictive maintenance models for...
ABB announces Dr. Jef Beerten as first winner of ABB Research Award
Dr. Jef Beerten from KU Leuven, Belgium, receives a US $ 300,000 grant over the next three years for ongoing research at the forefront of energy...
ISA and Beamex join to host flowmeter calibration webinar
The webinar, which will be held November 17 from 12-1:30 PM EST, will feature three automation experts: Nicole Meidl, Product Management Engineer,...
Nordson to introduce 3 new process solutions at The Assembly Show
As part of the exhibition floor at The Assembly Show, with over 260 exhibitors, Nordson EFD (Booth 821) will feature live demonstrations of several...
Protecting Industrial Control Systems: An Integrated Approach
By RKNeal, Inc.
The purpose of this whitepaper is to present a novel cybersecurity framework for deplaying and managing cyberthreat management...