ABB adds SIS to Natural gas dehydration facility
Located near a field of producing wells in western USA, the facility has safety critical points at each of several manifolds that share the total flow of raw gas being processed. One such manifold, as indicated Figure 1, has gas inputs coming through pipes from five wells in one area of the well field. Gas from the wells ranges in pressure up to 3,000 psi in insulated, underground pipe specified for these high pressures.
Removal of free and entrained water is done in two consecutive process steps. Both steps occur in pipe and vessels rated at 1,600 psi, which must be protected from possible pressure excursions at the manifolds. Once free and entrained water is removed from the natural gas, it flows via pipeline to another plant that separates it into such products as methane, carbon dioxide, hydrogen sulfide, nitrogen, and helium. Dehydration and separation of the raw gas are normally continuous processes occuring in sequence.
Originally, the dehydration facility operated with a basic Distributed Control System (DCS) to reduce gas pressures at the manifolds to 1,500 psi, as required to remove free water. The facility depended on pressure safety valves installed within the downstream process areas to shunt any overpressure gas to a flare stack.
Protecting lower pressure equipment
Growing demands for natural gas resulted in upstream supply pressures at the manifolds to near the maximum allowable. At this point engineers conducted a risk analysis study that indicated need for independent SIS protection at piping locations vulnerable to serious overpressures. The risk study also determined that a Safety Integrity Level (SIL) of 2 would be sufficient for all the components of an SIS -- sensor, logic solver, and final control element.
In this application, the SIS sensors are a pair of electronic DP transmitters from ABB to measure each critical pressure point -- set at 1,510 psi on a PLC SIL 2 logic solver. The final control elements are ball valves installed in each high-pressure supply pipe -- two valves in series to provide proper SIL for safety shut-off in case of overpressure.
The facility chose ABB 2600T series pressure transmitters having SIL-2 ratings certified by the German test agency TÜV. SIL-2 pressure transmitters work in pairs to monitor safety critical points. A pair of ABB SIL-2 rated pressure transmitters offers the same protection as three redundant conventional pressure transmitters.
Generally the installed and operating cost of specialized transmitters is far less than that of the required conventional transmitters to meet a specific SIL value. Set at 1510 psi the SIS catches an overpressure condition and shuts the ball valves in the high pressure piping within affected manifolds. This action takes place before any pressure safety valve vents, eliminating this possible source of undesirable emissions.
ABB is a leader in power and automation technologies that enable utility and industry customers to improve their performance while lowering environmental impact. The ABB Group of companies operates in around 100 countries and employs about 107,000 people.
MORE CASE STUDIES
FIPA delivers machine handling for Foilpuller automated sheet metal system
Featuring cycle times of 30–45 seconds, the CNC-controlled Foilpuller with FIPA EOAT and vacuum technology automates the film-removal process for...
Casa Systems chooses Omnify Empower PLM software to manage engineering products
Casa Systems was growing and they needed to find a solution to support formal engineering change control processes in order to eliminate issues...
Carolina Color chooses Liad to automate color delivery product line
Carolina Color faced an interesting business decision arising from the launch of two new coloring technologies. Carolina Colors decided to find an...
Rotork provides automated shut-off for heating pipelines in Northern Sweden bridge
Opened in 2014, the 2.1 kilometre bridge also carries two 400 mm diameter district heating pipelines which are now protected by an emergency...
Lakeview Farms uses Leading2Lean's CloudDISPATCH system to cut downtime by 34 percent
Six months after implementing Leading2Lean’s CloudDISPATCH system, however, Lakeview Farms experienced a 34 percent decrease in line downtime, a...
Wireless Switches & Sensors - New Control Possibilities
By Steute USA
Clearly, wireless technology has been widely accepted and embraced in the industrial community. This has resulted in the development...
Schneider Electric recognizes 50th anniversary of SimSci process simulation solution
SimSci process simulation solutions serve 23 of the world’s top 25 petroleum companies; 48 of the top 50 chemical companies; and all of the top...
Endress + Hauser earns IACET accreditation for IACET Continuing Education Units (CEUs)
Upcoming classes in 2017 which offer CEUs at Endress+Hauser include I-101 Basic instrumentation in January, March, June, and September in...
Empowering the Workforce to Control the Future of Automation
By Peter Martin, Schneider Electric Process Automation
Connected products are expected to approach 30 billion by 2020, with utilities,...
Okuma to highlight automated machining advancements at NTMA Plant Managers Roundtable
The NTMA Plant Managers Roundtable at Modern Industries in Phoenix, Arizona will discuss the various types of automation devices that make...